The blower is making a horrible noise -- sounds like bearings to me,
but on the net I saw mention of possibly some water? This is the
induced draft assembly, not the big squirrel cage at the bottom. The
blower is right in front of the firebox.
Depends if you have a 80 percent or 90 percent furnace as to the draft
inducer seeing condensate or not. If you dont hear a 'swishing of
water sound' then you can rule that out. If the sound is a high
pitched sort, then it does appear the bearings are failing....although
I found a small dead bird in a draft inducer assembly which created a
higher pitched whine. Shut off the power to the furnace then turn the
inducer fan by hand/small screwdriver ....and see if you can duplicate
the sound with the power off. Its more than likely bad bearings which
requires replacedment of the entire draft inducer assembly : $$$
On Thu, 18 Feb 2010 19:43:12 -0800 (PST), " email@example.com"
I would have sworn my draft blower bearings were bad on my furnace so
I took it off to check and the bearings were PERFECT. The chirp was
still there, so I looked more deeply into it - and noticed a bit of
red "rust" around the hub of the blower squirrel cage. The disk of the
blower was just a bit loose in the hub - the crimp was bad.
I hit it with a bit of brass and the acetelene torch and no more
Just goes to show you sometimes need to look for the unlikely.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.