I bought a GFCI extension cord a few months back. It's about 2-3 foot
long with a triple plug on the end and the GFCI works mounted in the
middle of th cord's length. Anyway, that stuff may not have anything
to do with my question, at least you know what I'm talking about....
I ran a heavy duty extension cord (about 40 feet long) from a standard
receptacle in my basement, through a window to the driveway and then
plugged the short GFCI cord into that, and then plugged my circular
saw into that. A friend who was going to be doing most of the cutting
(who is also a union electrician) saw this setup and told me I needed
to move the short GFCI cord so it was plugged into the house
receptacle and then the heavy duty extension cord could be plugged
into it, otherwise, the GFCI would not work. I told him I thought he
was wrong, but since he was doing the cutting (free labor, I might
add)I would hook it up any way that made him happy.
So now I am just curious, does this make sense? I know I've seen
these devices hooked up on jobsites at the end of a long extension
cord, just like I had it. And also, I would think if this were true,
it would have a big bold warning printed on it saying so.
What do you guys think?
I think your electrical guy was correct.
In this instance the GFCI is measuring the LOAD side of it's cord.
Therefore if there is problem in that short distance between the GFCI & what
is plugged into it will be detected, but if there is a problem between the
basement outlet & the GFCI it will NOT be detected.
If you plug your GFCI cord into your basement outlet and then your extension
cord into that you are effectively increasing the load side length of the
Politicians & diapers are filled with it & both should be changed regularly.
It's a safety thing. By putting the GFCI at the source, the extension cord
is also protected. _Never_ use a non-GFCI protected extension cord when
doing construction work. You never know if the extension cord has been
previously damaged or gets cut while work is in progress. If you saw it
done the way you described on a jobsite, it was probably to take advantage
of 3-way tap (not the GFCI feature) and the extension cord was then plugged
into a GFCI protected outlet at the temporary power panel.........if not
it's a serious OSHA violation, not soon to be forgotten if one has to pay
the fine......or worse, if someone gets seriously injured or killed.
firstname.lastname@example.org (DougB) wrote in message
SNIP I ran a heavy duty extension cord (about 40 feet long) from a
OK, so he was wrong if he was saying the GFCI would not protect him
while he was working the saw. But it made sense in that if the
extension cord coming through the window got ripped open, it could
energize the metal window frame and not kick the GFCI further down the
line (although it would probably kick the breaker at the panel).
So it does seem like a good idea to put it at the receptacle rather
than at the end of the extension cord.
The use of the 3 outlet splitter is exactly why I thought to put it at
the end of the extension could.
This makes me think they should not make the GFCI things with multiple
plugs at the end.
Thanks for the information.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.