Hi, and TIA for any help.
I'm attempting to install a new ceiling fan. I bought the special
bracket for support, but when I went into the attic today here's what I
found. The current electric box is metal and octagonal, and is mounted
to a 2X4 (via a mounting bracket with four nails). The two by four
runs perpendicular to the joists and is held in with four nails as
well. I was going to try to replace the nails with screws, but due to
space limitations I couldn't get the strength to remove them without
destroying the box. They extend all the way through the 2X4 so I
pounded them down at right angles, to make it more secure. I couldn't
budge the 2X4. The question is do you think this is secure enough?
The fan weighs about 20 pounds, 44" blades. It seems very secure, but
nails just tend to worry me.
On 17 Jun 2006 14:22:35 -0700, email@example.com wrote:
If you can't budge the 2x4, it should be fine. If it would make you
feel better, add a couple screws inside the box and into the 2x4. The
current situation sounds like the electrical box was mounted securely,
and to code for installing a ceiling fan. A 20-pound fan is not
It sounds to me like the existing box may already be a fan support box. If
it is it will say so inside the box. The big difference between fan support
boxes and standard boxes is that fan boxes use 10/32 screws for mounting the
fan bracket. Standard boxes use 8/32 screws. Since the box is secure, I'd do
what the other post suggested and run something through the box either into
the 2x4 or add another piece of 2x4 directly over the box
Here is an option to make it more secure. Cut a piece of 2 X
4 to span the two joists above the box. Drill a 3/16 hole or
two through the 2 X 4 that will line up with holes in the
box. Use 3/16" threaded rod and nuts to support the box.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.