It has recently come to my attention that I have a slow leak somewhere along
my water line. I suspect it is a couple of feet from the meter, due to the
fact that there is a slightly sunken area in the lawn and that the grass is
a slightly different color. The leak meter on the meter turns slowly, even
after the main valve in the house is shut off.
My question is, can this be easily repaired by myself, or is it best to call
someone. I'm leaning towards the latter.
Nobody can really say, if it is a pinhole leak a pipe clamp may work,
perhaps a wrench was used in that area long ago thinning-gouging the
pipe. Or it could all be about to go as it is old and deteriorated. Dig
it up and see.
Its going to be a hassle for you to dig up your yard amongst tree roots
(?) / rocks / clay (?) etc... , get the village water dept to come out
and shut off your water at the street, you make the repair (solder ??) ,
have the water dept come back to turn it on, maybe it will still
leak...etc.... In my opinion, some jobs are best left to contractors
who have the experience , will hopefully do it right the first time, and
give you a written warranty for thier work. Id ask around for a
reliable , honest Plumbing Company.
you don't have to call the water dept , turn the main off yourself.u only call
them if your shut off for no pay. Anyways , dig up the area u think is your
leak , when u find leak, if it's pvc Smile cause the rest will be a breeze. if
you find copper hmmm just find your leak first
Yep, sounds like galvanized and you'll almost certainly (as someone else
noted) need the line replaced...problem is, when you try to
repair/replace one joint, the joints are so corroded often one can't
break them apart w/o tearing up the next pipe section too. Plus, if
there's a leak in one place, there's bound to be more in the future.
I'd suggest finding the leak if you can and see for sure what it is...if
it is galvanized, I'd probably call a service and plan on replacing the
whole feed line w/ plastic and not even bother to repair the
existing...simply dig the trench and lay new line beside the existing
and cut if off and abondon it in place...
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.