The are two counter plugs that stoped working, I put the breaker back on..
there is power in the plugs but nothing works in them so i replaced both
plugs and the same thing..My little tester shows there is power there.. You
think the one breaker is broken?
If the breaker is on and you have power at the outlets, but they still don't
work, you likely have an open neutral conductor. If there are other kitchen
outlets on that same circuit that do work properly, the loose connection is
likely in one of them
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.