I always use 1.0mm T&E to an unswitched fused spur. You can use fle
but I find it difficult to terminate in the spur. You will only requir
a 1 amp fuse in the spur as even in alarm the system will draw no mor
than 600 milliamps. Take the supply from a ring main if you can, if no
a lighting circuit will suffice although I don't recommend and never d
it myself. Anymore info required let me know. I've been fitting thes
panels for years
The max current an alarm takes is tiny - after all it will run for a long
time off a small SLA battery when the mains fails. So 0.5mm flex and a 3
amp fuse will be fine. If you have larger flex lying around and it fits
the connections etc use that - it won't do any harm.
*Rehab is for quitters
Dave Plowman firstname.lastname@example.org London SW
Is this of any use: http://www.securitycentres.co.uk/Manuals/9448.pdf
And I agree that Scantronic are spectacularly unhelpful. Did they tell
you to contact your 'competant installer'?
I asked them about what type of PIR to fit to my 9449 panel without
success. Pyronix (the PIR supplier) were much more helpful.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.