I'm doing some plumbing for a friend and ran into the following
problem. After testing all of the roughed in water pipes and valves,
it was time to hook up some fixtures. I turned off the hot and cold
stop & waste valves in the basement and, starting with the cold side,
loosened the little valve on the side to drain the water. It seemed
like it was taking an awfully long time to drain and then I noticed
that the water coming out was hot!
So, I have an unwanted loop somewhere, and I'm wondering how to go
about finding it. I assume it's through a valve, and my prime suspect
is the washing machine valve. But there are other possibilites --
Any suggestions on the best way to troubleshoot this problem?
Thanks very much,
I assume the problem wasn't there before the rough-in, right? If
that's true, then the pipes you installed are somehow crossed. To
eliminate your hope that it's the washing machine, shut the hoses off
I think you either ran a hot water line to a cold outlet, or you
somehow looped them together.
Of course, it could be something freaky, like a recirculating line,
but these aren't usually put in home installations. If you do a little
more detective work, please write back with the info.
turn off every valve in house
shut off the cold inlet valve to your hot water maker
turn on the main cold feed.
go turn on each valve one at a time and see if one of the hots comes on.
I pipe my hot water supply as the first tee in my cold main, I can shut a
valve and have only the hot turned on. I dont know how you have piped your
system or valved it and if it is possible to have the hot on without the
cold being on.
But you should be able to check with the cold only on.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.