I was rewiring an overhead light receptacle in my unfinished basement
to be an outlet so I could plug a flourescent light into it. I didn't
turn off the juice while I was doing it and the hot lead touched a
nearby metal heating duct for a few seconds, taking the circuit out.
The circuit has mostly basment lights on it, although there are a few
lights on the first floor.
The circuit breaker didn't trip. I reset it anyway - no power. I
replaced it - no power. There was a GFI on the circuit which I
couldn't be sure was working properly, so I replaced it - still no
There was no smell of burning nor any visible evidence of burning or
scorching on the visible part of the circuit in the basement.
It was then that I noticed that a light in the garage, which is in the
beginning part of the circuit, worked with the breaker on.
Is there anything I can do or test for, or should I just call an
Somewhere in the circuit there's a connection of the hot
leads (probably a wire nut) that arced and is now an open.
Odds are it's either in the box behind the light that _is_
working, or in the box behind the next device in the circuit
that _isn't_ working.
I'd suggest killing the breaker this time to work on it.
What he said, but also... You just have to go from device to device.
Between the last point you have voltage,and the first point you don't is an
It's good you replaced the breaker; it should have opened.
Yeah, but from the info we have one of two scenarios happend:
1. The flaky connection didn't allow enough juice to flow to trip a good
2. The flaky connection, though bad, wasn't all that bad, and the
breaker should have tripped but didn't.
I'd replace the breaker on general principles. A few bucks at the borg,
in exchange for piece of mind.
Of course, my next concern would be: what else was messed up by the
I hope I'm not violating protocol by expressing my thanks for your
responses to my wiring problem.
I finally noticed scorch marks on the light switch that controlled the
garage light (even though it worked). Opening the box (with the
breaker off this time!) I saw that the hot wires were connected at the
switch and had melted the back of it. I replaced the switch and the
entire circuit worked.
Thanks a lot. Your comments gave me an idea of the direction in which
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.