I am the second owner of a home built in 97. The trane wreck is orginal
equipment. It is a outside located heat pump. Why is copper connected
to aluminum tubing coil. Looks like low quality construction. This is
very poor as most are expected for 15 years from what I have read.
The repair man said he found numerous leaks in the outside unit,
however He only check the outside unit based on the most recent charge
only lasting 30-60 days. Repair man said numerous of these units have
I do not currently have a problem with pricing, however what bothered
me is he said if I wait till after January I will be forced into a 13
SEER unit. That did not bother me much either. What make me not want to
go forward with this contractor is that he want to run the tubing up
the side of the house with >12SEER unit.
Why can he not cut a larger hole and use the concealed tubing? It
currently runs under the house, up the wall and over to the utility
room over the garage. I do not want a high bill AND an ugly house.
He is not quite right. After January 23, it is illegal to MANUFACTURE
anything less than 13 SEER. They can still be sold & installed till
they are out of stock.
Trane equipment normally lasts 12 to 15 years here in Myrtle Beach SC.
Trane uses aluminum tubing with aluminum fins in a very reliable coil
that has stood the test of time. The rest of the unit uses copper
tubing, hence the transitions.
If the leak has been found in the outdoor unit, why is he replacing the
line set? If the line is too small, that is the only reason that I can
When I must replace a line set in that manner, I normally run it inside
a downspout that matches the downspout on the house if there is any.
Normally, to get a true 12 SEER, the indoor coil or indoor unit must be
replaced also. Make sure you get an ARI certified match.
This guy sounds pushy to me. He is probably on commission. You may
want a second opinion. You may also want the indoor coil checked for
leaks as well.
Normal doesn't apply when poorly contstructed fittings are used. Copper
is factory annealed to aluminum tubing. That is just low cost
contruction that is intentionally unrepairable and what many people
call junk. These units have had numerous similiar complaints, but only
claims the new units are improved.
I think the HVAC rep was more greedy than pushy. A ten minute search
found the Goodman unit for 478 undelivered. He wrote a quote to replace
the coil 10 SEER, Unit Quoted and install for 1875. Three other calls
to local repairmen had two no shows and one no call back. I can only
assume I will get the same service in spring. I got a guy in our
maintenance to install the 10 SEER Goodman, and a recharge for 140.
I wish other would go the same route if presented with the service I
I'm sorry, but why are you asking any body here how to run the AC line set??
It is not like we can see your house from here!! Nobody here will be able to
tell you how to run a line set into your house! We do on occasion run line
sets up an outside wall. There are products available to conceal the line
set so it looks no worse than a down spout.
If you don't like what he proposes, call someone else to get another
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.