1 circuit -Fridge 1 circuit -Microwave/Range Hood 2 circuits- Counter top outlets
Now I have to address the lighting issue. Presently I have one fixture in the middle ( which is coming off a 20A bathroom circuit). I am adding at least 4-6 hi-hats in addition to keeping the middle fixture. My intention was after I tear down the walls and ceiling to re-wire the lights the right way to an existing 15A lighting circuit, but in the event I can't find one nearby, what are my options?
1-Keep it on the existing 20A bathroom circuit 2-Tap off one of the 4 circuits I'm running for the kitchen
The panel will be pretty full after running the 4 new circuits, so running a seperate 15 A line is not an option.