# Three way switch - FIXTURES IN MIDDLE

av wrote:

yes that's what i presently have.

i know! did i mention that i only have pancake boxes installed for each fixture? i *might* be able to change that, depending if i can find other fixtures that would accept them.
oy, what a mess!!!
but thank you! av
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Your fixtures boxes at present have 6 conductors in them. Assuming they have an integral cable clamp, then they should be a minimum of 16 in^3 in volume for 14 AWG wire, or 18 in^3 in volume for 12 AWG. I don't know how big your pancake boxes are, but I doubt they are 16 in^3 in volume.
It sounds like you have much more basic problems than your 3-way switching difficulties. You need to change all the boxes to something bigger. Perhaps while you are doing this, you can change the existing cable runs from 3-conductor to 4-conductor by using the 3-conductor cable to pull new 4-conductor cable (or two 2-conductor cables). If you do this, you'll have 8 conductors in the fixtures boxes, so they need to be at least 20 in^3 for 14 AWG wire or 22.5 in^3 for 12 AWG wire.
Cheers, Wayne
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Is now a good time to mention... Jewtrals? :-)
<~~~running and ducking
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
On 6 Jun 2004 15:06:51 -0700, snipped-for-privacy@sover.net (av) wrote:

Whoa! Wait. Are you adding fixtures or switches?
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

that was a mistake on my part. hasty writing amidst anxiety of problem.
ok... thread is closed now everybody.
av
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

## Site Timeline

• ### "correct" way to prep walls for tile in shower?

• - next thread in Home Repair
• ### Power to microwave oven goes off and on

• - previous thread in Home Repair

• ### Wing mirrors on cars

• - last updated thread in Home Repair
• ### steam bending

• - the site's last updated thread. Posted in Woodworking Forum
• Share To

HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here. All logos and trade names are the property of their respective owners.