Are there any particular noticeable signs of a submersible well pump going
bad. In the past couple of weeks, I've noticed that when it cycles on, I
hear three or four "knocks" in the pipes as compared to just the one when it
first kicks on, as it used to be. If I hang out by the pressure tank with
my hand on the incoming line, I can actually feel these surges like the pump
is actually going on and off a few times. I had something similar a few
years ago when I had small holes in the galvanized pipe coming out of the
well. In that case, I would get spitting when I had the water on, but
that's not the case here. No spitting, I just get the noise. Also, I had
the galvanized replaced with plastic back then also.
Any ideas would be appreciated.
I'm not a pro or expert here, but have worked on a few systems in my
life. The pump would be the last thing to suspect--there's no switches
or contacts on the pump itself, so it will either run or not run. A
possible exception would be a bad wire splice at the motor which has
worked loose over time, giving an intermittant connection but this is
unlikely if the system was professionally installed.
First thing to check is the pressure switch, which would be a plastic
roundish rectangular box mounted somewhere in the vicinity of the tank
inline with the piping. That's what turns the pump on when the pressure
goes down to a preset limit, and off when the line pressure goes back up
to 40 psi or whatever pressure limit the installer set it to.
Pull the cover off the pressure switch, give a visual check for rusting
or loose connections, and monitor it when the pump cycles on. The
contacts may be badly pitted, or the mechanism may just be wore out if
more than 15 years old. They're about $25-30 at a plumbing supply. I'd
recommend a plumber to check it out and replace if necessary, since
setting the pressure limits on the unit is kind of tricky
I'm hesitant to give this advice--but if you are comfortable working
with electrical stuff, you can use a plastic chopstick or disposable pen
tube to hold the contacts closed right after the pump starts, just for a
few seconds. If the pump does the same thing, the next thing to check is
the control box which contains the start capacitor and relay. It's a
rectangular metal box about 4" wide, 8" long, and 2" deep and there
should be an electrical connection between it and the pressure switch.
The cover pulls off (AFTER YOU CUT THE POWER SUPPLY) and you can take it
to a pro to have it checked out on a meter. Some of them give
instructions for doing this inside the cover, using an ohmmeter. They
are about $50-60, not cheap but if just the capacitor is bad you can
replace that for about $10. That's a black plastic cylinder with wires
connected to it.
Otherwise, if your pump is older than 15 years it's nearing the end of
it's rated life and getting time to think about replacing it.
If you don't have more than a basic familiarity with electrical stuff
and don't know how to protect yourself from electric shock, disregard
all my advice and call a pro to check out the pressure switch and the
control box. A well pit is one of the most dangerous places to do
electrical work because it's so easy to be grounded at any part of your
body. In fact, disregard it and call a pro anyway--I'm just telling you
what I would do.
One of the things that would check is the circuit breaker itself, which
powers the pump. A breaker which is going bad can deliver erratic voltage,
and cause problems. You would want to check the voltage coming off the
breaker while it is under load (the pump on). It may be easier to just
replace the breaker, if you are able to do that yourself.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.