On Sun, 09 Jul 2006 15:23:28 -0400, email@example.com wrote:
I agree. A ground is a ground is a ground. Both subpanels as well as
all wires in junction boxes should be connected together and all of
them to the ground rod(s) too.
Yes, neutrals are a different matter and should be fed from the same
source as the hotwire.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.