I have a Lennox HS-18 Heat Pump. I recently had a problem with a dirty
air filter and was told if the same problem occored again to open the
outside unit and press the red reset button. The problem was because of
restricted air flow the unit sensed a problem and shut down the outside
unit, leaving the inside blower blowing cool air continuosly.
I changed the filter and reset the switch. When I do that I hear a
clicking noise on some sort of a switch above. But this switch never
actually makes contact to allow the unit to go on. If I touch the
switch it will make contact and work, however once the temp gets to the
thermostat setting the unit goes off and won't go back on.
Does anyone have an idea if I am doing something wrong or does this
sound like another problem? I plan on calling the serviceman again but
I wanted to check here as well!
Also, anyone have a ROUGH idea how much a complete new unit installed
might run? This thing seems ancient and inefficient. Just a ball park
figure would be appreciated!
You shouldnt have to be resetting a switch to make your unit run
Hint # 2
Your serviceman is an idiot. Call a different one. Preferably, one
that can read and diagnose refrigerant pressures.
Which ball park should I base this on?
I'm not sure what to make of what he told me, I am relatively new at
heat pump understanding. My unit appears to be pretty old. I had been
buying Naturalaire MERV 10 filters and I changed them last year every 3
months with no problem. This year I had one that was 1 that was
slightly over a month old when my original problem started. He "reset"
the outdoor unit and I replaced the filter. The next filter only lasted
for 3 weeks. I was told that I should never use MERV 10 or MERV 8 in
the winter and he put in a cheap blue fiber filter and told me to only
use these. I could use the others in the summer if I wanted to. Last
winter was much colder and I had no problems whatsoever. Unfortunatly,
I am in a new town and don't have many people to get references from. I
am posting so I can get feedback on what they are telling me and learn
for myself. Does the filter scenario sound right to you? It didn't to
me. I have had dirtier filters last year that didn't stop the outdoor
unit. Thanks for your input!
Without bashing the tech too bad, how about if I just say, "He just
may not understand refrigerant, filters, pressures, air flow, high
pressure switches, electricity and customer knowledge. Maybe he is
just really a painter?
You may want to look into your condo assocaiation for answers. Maybe,
if they have monthly meetings, attend one and ask those in there who
they have used in the past and their experiences?
Thanks, that makes sense, something doesn't seem right with that
switch. My unit seems to be pretty old. Almost every unit in my condo
complex has these same units and they all appear to be old as well.
Probably people don't replace them because they don't intend to live
there for a long period of time. I'm not sure if I want to replace or
have someone better come check this from top to bottom and assess it.
It must be an HP18 to be a heat pump. An HS18 is a straight air
conditioner. That system was rated around 8 SEER.
Those high efficiency pleated air filters ar highly restrictive to air
flow. This will cause the compressor discharge pressures to run high
in the heating season, often high enough to trip the high pressure
switch. It will be worse in mild weather, which is why you are having
trouble this winter. Pleated filters often reduce air flow as much as
20%. Go back to the cheap blue filters. If you must have pleated
filters, put in a new system with a variable speed indoor blower unit,
as they generally are a more powerful blower.
Prices for a new system will vary with brand, size, efficiency,
contractor, and area of the country. If you live in LA, it will
generally be more expensive than if you live in the boondocks. If you
need duct mods, that drives the prices up. My prices vary from $3500
to $10,000 depending.......
That would be entirely up to you. Someone "better"? Yes, definitely.
BTW, if the system is problem free, then you should be able to use any
type of filter that you want to use. Putting in a cheapo fiberglass
filter isn't a fix, it's a patch. It
s a bad patch at that, since it will allow additional dirt to accumulate
on your indoor coil, and a dirty indoor coil is very possibly already
the cause of the excessive head pressure.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.