I'm trying to find out if it is possible to tie in the wiring for a new
The existing box has a 3 way and 2 way switch. I was thinking I could
replace the 2 way with a double switch to control the existing light and
If this is possible what is the wiring configuration?
All neutrals should be connected together and non should be connected to
a switch. I find it difficult to visualize exactly what your mean by your
description so I can't really comment on that. Part of the problem is there
are a number of ways of wiring such switches. I might also say that it is
OK to use the neutral between three way switches as runners, but the ends
should be marked with tape or paint. Often they are not. This makes it
difficult to figure out how to wire any changes and is a sign of a
incompetent wiring job to start with.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.