All of you pathetic! what in the world noise generated in condenser
had to do with expansion valve on the evaporator,
if you happen to have head master valve I would say it is head master
however I don't believe that there is one so? the problem is in compressor
internal relief valve is must likely culprit it is relieffing pressure
when pressure get high on hot days but you are to bloody arrogant to admit.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.