This was enough better that with comparable temperatures I used half of kilowatt hrs 2nd 2 weeks than 1st 2 weeks, but I still think it can do better. When heat comes on & blower is starting slow, air out of registers is quite warm. As blower ramps up air cools down.when blower slows down before it quits, air is warmer again. It only makes sense if blower didn't get up to 100%, air coming out of registers would be warmer longer.
My question is how can I set dip switches so blower only goes up to 50% or so. And I'd like to know if this could be a problem? Thank you.