i may have made a mistake, buying unused but open parts on Ebay
replaced the doorbell chime box, and the outdoor push button,
and now i get sporadic results -
sometimes it works and sometimes it doesn't work,
and sometime it seems to work halfway
well, my question is simply - could it be the Transformer?
does a Transformer either work all the time [perfectly], or never?
Some transformer for heating are rated in volts,
and also VA, which is volts times amps. Possible
the transformer isn't able to handle the current
Christopher A. Young
learn more about Jesus
On 10/1/2015 1:21 PM, firstname.lastname@example.org wrote:
Chances are, you've got a bad button -- or bad wiring job.
Is this a genuine *chime* -- i.e., a solenoid that strikes a
sounding bar? If so, remove the cover and observe the "plunger"
while pressing the button (or, have a helper assist). Is it
moving ALWAYS? Or, getting partially hung up? Or, only
moving *sometimes* (requiring you to jiggle the button
while pressing it)
On 10/01/2015 03:21 PM, email@example.com wrote:
Not likely to be an intermittent transformer.
Have someone press the button while you look at the chime.
If it moves a bit but does not chime, then it's probably bad...
but it would not be a bad idea to actually measure the voltage on the
output side of the transformer. I've seen some that are dual voltage 10v
/16v ac and it's possible you have a 24v chime.(or at any rate a chime
connected to too low of a voltage)
On Thursday, October 1, 2015 at 1:33:22 PM UTC-7, philo wrote:
i'll have to check the voltages, on both the trans & chime box.
house is 7 years old or so,
and the old [one sound] doorbell was way to low to hear upstairs.
I wonder if that tells anything - the low volume...
So, i've put in a newer fancy [10 sound option] chime box [IQ America]
and a new outdoor push button, with sporadic results
On 10/01/2015 03:49 PM, firstname.lastname@example.org wrote:
If it's an electronic unit it's not a case of a "hung" solenoid but
still I'd make sure the transformer is providing the correct voltage.
Just checked my transformer...it was installed in 1932 and still works fine.
I guess original one was El Cheapo one. Now your fancier one which
probably needs more juice. Our house has rotary gong with 5 tube sound
tubes. Can have 3 buttons front, rear and side door. Front door plays
Westminster chime. I don't like digital synthesizer type. Un-natural
sound to my ears. WAs old button lighted one? New one too?
One < fairly easy ? > trouble-shoot for this sort of thing -
temporarily " install " your old chime - with patch cords ?
- see if it works OK with the new pushbutton. and/or
temporarily install your old pushbutton - with your new chime ..
.. a couple RAGs < random-ass-guesses >
closely examine - look & feel & wiggle the wires at the pushbutton
and at the chime for looseness / damage / nicks / etc
Check that the pushbutton housing wasn't deformed slightly
when screwing it in .. they are often quite flimsy ..
Good luck - let us know what you find.
On Thu, 1 Oct 2015 13:21:28 -0700 (PDT), email@example.com wrote:
I'd suspect a bad button. Remove it from the wall, take off the wires
and touch them together. If the bell rings, you know the button is bad.
You can safely do this without getting shocked. It's low voltage!
If this dont work, then you know the button is probably good and either
the bell or the wiring is bad. Transformers seldom go bad on doorbells.
If they do burn out, they wont work at all.
Of course be sure the voltage is correct on both the bell and the
On Thu, 01 Oct 2015 20:09:42 -0500, firstname.lastname@example.org wrote:
This is USUALLY the case, but I have had small transformers like bell
and thermostat transformers that were, for lack of a better term,
FLAKEY. Work fine cold, and cut out when hot, or drop output voltage,
due to shorted secondaries (a few turns shorted - only when hot, 0r
just plain intermittent.
Not common - not the first thing I'd check, but I would not discount
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.