We have an overhead alarm cable which runs between the two buildings at our
site. The cable runs from just below the roof of the two-storey building to the
base of the chimney breast on the single storey building. It is protected in
conduit attached to a metal catinery cable.
My query is that the conduit hasn't been run right up the brickwall of the
two-storey building and does this constitute a violation of BS4737?
There is a gap of about 10cm where the cable isn't protected, whereas on the
single storey building the cable enters the building via a circular JB and is
You help would be appreciated.
Remove NEWS to reply