Wondering if anyone out there has seen any information about using a
standard, or high efficiency, LP domestic hot water heater as a heat
source for a small radiant heating application? We have an application
where a customer needs a temporary heat source for a small addition with
a heat loss coming in at 28Kbtu's. There will later be a central boiler
on site but the addition will need to be heated in the interim. We are
thinking a 50 gal. high efficiency LP water heater, closed loop,
providing no DHW (feeding the radiant only) may work. With the radiant
loop containing only 7 gallons of water and most LP units coming in
around 40kbtu input it may be doable but looking for input.
We are trying to avoid a small HE boiler for such a small space and a
it works great, I have set up a few of them.
I have always wanted to put wheels on an on demand hot water maker to have a
portable heating system.
I like a primary/secondary loop setup, but where you are temp you might be
able to skip that.
Thanks for the reply,
So by primary/secondary you mean run the DHWH at a higher temp. and
pull the radiant off with a thermostatic mixing valve at a lower temp? I
had considered this as an option if the DHWH only has a low limit of say
100deg. F (too hot for radiant).
This would surely be the way to go if the DHWH was providing potable
hot water in addition to supplying the radiant loop or perhaps to boost
I am thinking where the heater will have a relatively high return water
temp. the recovery will be much higher than the 40gal/first hour most
call out when using city 50 degree city water.
Thanks again for the input,
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.