how many wires can you run through the same hole in a stud /joist /rafter.
figure the hole 1" or 3/4" and you are useing 14/2 or 12/2 is there a set
amount or just what will fit without having to force them and how often can
you repeat this on a run.
I really thought one of the "code guys" would respond to you on
this. Yes, there is a limit. It has to do with heat. Some inspectors
are more concerned with this than others, but it is in the book.
AFAIR (and I'm not a code man) the 3/4 would be OK for one wire,
you'd need at least 7/8 for two. That's off the top of my head.
Ask the local inspector - you don't want to have to redo it.
If you're using modern 90C wire (e.g. NM-B not plain NM), then you can
usually run 9 current carrying wires in a raceway or bundled together before
you have to derate the ampacity. You won't get more than 3 cables (6 current
carrying wires) through a 3/4" hole. If you use 1" or larger holes, don't
run more 4 cables through holes if the run is longer than 24 inches.
If you can, I'd avoid holes larger than 3/4 in 2x4 studs and rafters so you
have over 1.25" between the hole edge and a face of the board. If its
structural (like a rafter), that is another reason to keep the hole diameter
down. If its an engineered truss member, don't drill it at all. Drill an
additional hole at least 5 inches away from other holes if you need more in
the same board.
Actually "cable in joist hole" limits are more a matter of the damage
you might do to the cable running multiple cables through a whole series
All that rubbing...
Heat dissipation is seldom an issue if you're only talking 1-3" worth
Indeed, some electrical books _encourage_ single-cable through hole practises.
I don't think the code books specifically talk about this per-se (other than
derating limits), but you could be subject to invocations of the "workmanship"
Precise details of where the holes can be is usually building code, and I don't
have a precise spelling of that out handy.
Perhaps more important, when you're doing long routings, is to do the best
you can to avoid kinks - keep the holes _straight_ as much as possible.
Angling in spade bits results in frustrating experiences and cable damage.
Properly perpendicular holes drilled with auger bits are a joy to work
I tend to prefer a 7/8" auger. Clean, two cables still fit easily.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.