Hi there ...
As if anything else could go wrong with my condo ...
Had an HVAC contractor out to look at my current furnace/AC -- some
labels had fallen off the coil into the drain pan AND he found out
they had not built a trap for the condensate drain line. He built a
trap down by the drain ...
I had the drain tubing from my water softener bungeed to that line.
He moved them off to the side (which is actually the way the manual
for the water softener shows it -- the drain tubes tied to a brick
over the floor drain.
Only problem with the way he set it up was during the "rapid flush"
phase my water softener would spray the base of my water heater.
I have subsequently moved the water softener drain tubing off of the
condensate drain and onto the pressure relief line from the water
heater which is just about dead center of the drain.
Problem -- I haven't had a chance to run it in this configuration but
I know during those two flush cycles it will probably have enough
pressure to splash all over the place.
Does anyone know of any more "permanent" ways to hook up these water
softener drain lines?
When I first got there they actually had them UNDERNEATH the drain
cover -- now I understand you're not supposed to do this because you
need an air gap so that waste water can't siphon back into your
potable water lines.
Any ideas will be appreciated.