Need some tips. Last year we had a new trane central ac installed. It's
worked great until today. Warmed up so I flipped on the A/C and while the
compressor outside comes on the fan never kicks on inside. The furnace works
fine if you flip it to heat. After the A/C was installed I put in a new
Hunter 44110 thermostat myself. I'm guessing it's probably the thermostat.
Is there an easy way to check this or should I just get a new thermostat and
see if that fixes the problem?
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.