I've just installed a totaline wireless thermostat P474-1100RF and
P474-1100REC in my home.
My old lux 1500 thermostat had the following terminals: G, Y, W, RH, B,
The wires from the furnace were connected Green to G, White to W
and Red to RH
and there was a thick black jumper wire from the RH to RC
The totaline has the following terminals: C, G, Y1, W1/O/B (all one
R, Y2, W2.
Common logic would assume that the Green wire goes to G, White to
W1/O/B and Red
The problem is that now when I try to get the heat to come on, the fan
for a minute and no heat comes out no matter how high I set
Any ideas about what I need to do, or should I call an HVAC
All ideas appreciated.
Thank you in advance.