Rain all day here. Might as well hit up some inside issues.
Outlet shows faulty wiring with one of those plug in outlet analyzers.
Here's what I found.
The "electricians" thoughts...if they had any at all:
Oh what the hell. They all connect back in the panel box anyway.
Oh here's an empty hole. It fits. Must go here.
Why use those pesky screws. Anyhow, they're kinda dirty.
Gee that backstabbed white might have unsheathed wire showing
because...it's lose and falling out maybe?
Wonder why the "electrican" didn't just backstab the ground on the
hot side. It's closer.
And further up the same line
The "electricians" thoughts...
Hmmm, broken wire. I'll just reattach to this screw securly. Let's
see. This screw is on the same side of the outlet as where it was. Must
be just another place to attach same connection. Lucky me they
backstabbed all the other wires!
The "electricians" new connection seems to be wrapped the wrong
The new connection has a kinked loop.
I don't think the new connections is even around the screw.
In the end I just threw out the outlets, cut bare wire ends off to
sheathing, restripped and attached to screws of new outlet. Green lights