*I was thinking in terms of saving labor. I thought it would be easier to
just cut off the old pipe and run 100 amp SE cable up instead of pulling out
the wire from the pipe, connecting another pipe, and then pulling the wire
back in again. If the SE cable got pulled away like the pipe did, it would
be easier to push it back against the building.
On Sat, 1 Oct 2011 08:06:02 -0400, "John Grabowski"
That is OK if you have one of those PoCo crimping tools to make the
splice but Polaris connectors would add another $100 to your project.
RNC has all of the ease of SE/SER, it is a lot cheaper and he can use
his existing wire.
*The OP stated in an earlier post that he will be undoing the connections at
the weatherhead to remove the existing pipe. Since he can kill the power
himself, he does not need to buy expensive insulated connectors or an
insulated crimper. You are correct that sliding a length of PVC down over
the existing wires would be the cheapest way to go and a lot easier than
working with rigid metal pipe. If the same accident happens again the PVC
may break though. I suggest some extra straps just in case.
In this case that is not true at all. The run from this maypole is on
the load side of the service point and the customer owns it. Actually
in most places the customer owns the service lateral from the street
anyway, even though it is on the line side of the meter.
The service point in most underground systems is where the service
lateral leaves the right of way.
The service point on overhead drops is usually at the service head and
the PoCo owns the drop (you own the wire down the side of the house to
the meter) but this is not a service drop it is a feeder and he owns
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.