This is a 3 year old home. Tempstar furnace and ac unit with a White
Last night we noticed the unit blowing cold air. I found the Ac
running.The gas is cycling when the house temp falls below the set
limit. I pulled the breaker on the Ac to stop the compressor. The
blower still runs constantly with the gas cycling as required. Any
suggestions on additional trouble shooting. I'd like to narrow it down
either to the thermostat or the main unit.
i searched google groups, maybe warranty coverage, see:
The outside condenser blower or the inside furnace blower.
If the condenser blower motor is grounded it can run at a low speed
Many things can cause the indoor blower to run constantly, --depends on
the furnace and the various blower control components.
Is the RM TH fan switch in the off position?
PROPER A/C UNIT & DUCT SIZING ESSENTIAL for EFFICIENCY & BTUH PERFORMANCE
Disconnect the wires to the thermostat at the furnace (remembering where
each went), turn the breaker back on, and see if it's still running.
If not, it's either the thermostat or the wires to the thermostat.
If it is, then it's something internal to either the main unit or the
compressor (my guess would be the relay on the compressor is frozen).
The e-mail address in our reply-to line is reversed in an attempt to
minimize spam. Our true address is of the form email@example.com.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.