Am wiring my new unattached shop. Running off a 60A breaker from my main
service panel. Supplier has a UF #6 - 3 conductor w/ground which would be
the easiest to install.
However, I will have a 60ft run with about 45ft above ground and 15ft
underground. It will run on top of my rafter joists through my attached
garage, down the wall, underground 15ft to my shop, and up into my shop.
Bldg inspector said it would be OK to run it on top of my joists without
conduit (if it's protected) & buried without conduit.
BUT the chart says it's only for use up to 55A. Do I have to go to a #4
conductor to get 60A out to my shop? That's alot of loose wire. And I'd need
Do they make a copper 'triplex' that will allow 60A that doesn't need
I suppose I could use a 50A breaker if I had to. If I could find one.