On Sun, 3 Jun 2007 20:52:24 -0500, email@example.com (HVAC fella)
Think real hard. Its really not that tough. Remember when you were a
kid and your mom/dad told you respect others and their belongings?
Then lets look at it this way:
Supppose you just shelled out $2000, $3000 or $4000 or more for that
Carrier R410a (it AINT fuckin PURON) unit for your home.
One day early on, you have minor trouble and a goof ball or drunk or
stupid or inexperienced greenhorn shows up to "fix" it.
He dumps in a pound or 2 or R-22 to your R410a system.
What are YOU going to do?
Yeah, I thought so. Now go do the right thing and dump the charge,
install a new drier (Rated for R410a), pressure test it for leaks,
evacuate it to 500 microns or whatever Carrier wants and recharge it
with NEW R410a. Tell the customer you made a mistake, send them
flowers, candy, gift certificate etc and tell them to have a great
The obvious question is why would anyone think a 410A system is a 22
that is low on charge unless is was nearly empty-- in which case the
original problem must be fixed first-- then drier replaced, evacuated
and properly charged with 410A. I could understand if the situation was
the other way around. Used to happen often-- dumping 22 into a 12 or 500
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.