only getting about 10 degree diffents between return air and vent air
71 and 81 but really hot day over 100
most of the time
68 and 78 when in the 90's still not right
low side pressure is about 70 psi
goodman split system and upstairs unit
downstairs goodman unit working alot better
Unit Capacitor went out about 3 weeks ago. A/C man came and replaced
it. He checked the R-22 and said it was good. At time I did not notice
the air different. When the Capacitor died i turn off the system for
the day. So when the A/C man came is was in the 90 upstairs. When he
replace the Capacitor cold air was coming out not sure of the degree
of cold air but it was cold so he left. Now i know I should have made
him wait to see how it could bring the temp down.
We replace the filters every month. New system, new house only 4 years
old. I also notice not much water come out of the drain pipe like the
unit downstairs. The one downstairs drips really fast. But then again
for now only use the upstairs to play on computer. Master bedroom,
bathroom, living room etc all day stairs. so may not be too much
What should I check? And what should I make sure A/C man checks when I
guess I will have to call him back.
Why do you have to put a new system in a four-year-old house?
Check your vasectomy to make sure you cannot reproduce.
And what should I make sure A/C man checks when I
Yeah, give him a long list of things you want checked and tell him exactly
what to do. Watch him like a hawk while he is there, and make sure he signs
off on your checksheet for each item and writes his initials and dates it.
measure the supply air temp just as it leaves the evap coil, then at
the grill furthest from the furnace. Both should be the same temp. If
not, replace, upsize, seal and insulate ALL attic duct work.
Now do similiar for the return air. Measure temp at RA inlet at
grill, and then at furnace/air handler. Both temps should be the
same. If not, replace, upsize, seal & insulate ALL attic duct work.
your attic duct system is leaking so much air and probably sucking in
so much attic air your poor ac cant begin to cool your upstairs.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.