I have a Frigidaire - FG6RA air handler that has been giving me
trouble for about a month.I will try to explain this as best I can.
Things I know:
The pressure switch must be open before the condenser comes on.
It must be closed for the burner to light.
I was having trouble in that the thing would cycle and the pilot would
glow but the flame would go right out. The error message on the board
said the the preasure switch was closed when the condenser started.
Fair enough. I spoke to some people and replaced the PS. It worked for
a few days and now it doesnt.
This is what I tested and the results:
I removed the leads from the PS. I hooked up the MultiMeter to the
leads to check continuity. When I turned on the furnace the meter
would beep intermittently very fast and the condenser would NOT come
on. It should be open, right. Then I pull the leads off and the
condenser DOES start. The only way it would work now is if I jump it
at this point. My Multimeter isnt completing the circuit is it??
I am realy at a loss and any help is appreciated
Well, lets see... by using his words.
Burner to light
Pilot would glow
Flame would go right out
Pressure switch was closed when the condenser started
When I turned on the furnace... and condenser would not come on
Pulled leads and condenser did start
WTF is he working on?
I know what a Frigidaire - FG6RA is, but come on, this dude has no business
messing with heating and cooling equipment.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.