I had to reset abreaker box breaker for my heatpump as the outside
unit stopped and the thermostat heat indicator just kept flashing. Can
a breaker wear out and not trip but still kill the power? I guess my
question is can a breaker show it's on but be tripped slightly?
excess of the breaker rating causing a thermal snap to release and
allowing a spring-loaded switch to open. Perhaps the spring in your
particular breaker is a little weak, so it has popped just slightly
open, just enough to break the connection. The breaker may be fine
otherwise. That is, it may be reacting to an excess of current flowing
thru the circuit, as it should. I'd mark it with a piece of masking
tape so you can locate it easily. The reason for circuit overload may
indicate a problem elsewhere, so you should not assume that the breaker
alone is at fault, although that is possible, of course. You may just
be experiencing some extreme weather conditions !!! causing the pump to
work a little harder than usual? Good luck with it.
Yes. I've experienced more than one breaker that was tripped but showed
no signs of it. This is especially interesting when working in an
unfamiliar building which has no labels (or inaccurate labels) in
multiple breaker boxes leading to endless hunting for the culprit.
Flipping the breaker off then on will reset it but in the long term it
needs to be replaced. Or I guess you could just live with it now that
you know which breaker is the problem.
Who knows. I've seen where the mearsure of a motor's amps is directly
proportional to power which is directly proportional to the amount of
work it is doing. So a clogged fan is moving less air(working less),
so the amps acutally decreases.
Now your compressor might have to work harder,so that is a different
tom @ www.CarFleaMarket.com
You should be aware that some breakers [I do not remember the brand(s)], do
not move the handle to the OFF position when tripped. In fact, they move the
handle slightly further to the ON position. To reset, you have to push them
hard to the OFF position, then back ON. Best Regards.
I breaker can fail, yes.
How they fail is usualy in different ways, but usally, from
experience, they try to fail in the safest mode they can.
Fail by tripping at lower set points.
Fail mecanically internally, but pop open permantly.
As for the red flag, that is something of convience, to help you
identy which breaker tripped. I've heard that will only whos under
some conditions, ie a short verses an over current.
Also, many breakers trip interally and have little/no movement of the
handle, this provides for the breaker to still open if someone is
trying to force it closed via the handle. trip-free.
So many what-ifs, sorry, not there to see what is acutally happening.
Truth is if you have concerns about any electrical you need to have
someone qualified to take a look at it. The 5 dollar breaker might be
opeing to protect a fault in you expensive heatpump, and save you some
So good luck with your investigation.
tom @ www.BookmarkAdmin.com
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.