I work and live in Memphis,and My company has been installing 13seer
units,this year,Well it seems that we get alot of call backs that the
units are not cooling as well as the H/O old 30 year old 10 SEER
Now I dont know if the installers are pulling vacuums or not,and I am
sure that the units are not charged by sub cooling either,So those are
a couple of factors to take into consideration.. It just seems that
these new 13 SEER units are over sensitive to hot return air,hot
outside tempratures,and proper freon charge..
Now on the older 10 SEER units,it seems that one could have a open
return in the attic,not pull a vacuum,and overcharge by 3 pounds,and
the thing would still cool the H/O's house down.. And these new 13 SEER
units,we have to lower the fan speeds,install TXV's on every last one
of them etc etc...
Basically I am just curious if any other service techs out there in
the HVAC world have had problems with these.. I have heard alot of
differnt things from other's,But not enough :P The new 13 SEER are
supposed to have the same capacity as the old 10 SEER,but have thinner
evaps etc.. Gonna stop here,untill I get a response for the question at
hand.... "Do they cool as well" ??
The couple of 13 seeers I've worked on, they tend to have rotary
compressor. LOTS of fins for the condensor. The new condensing units
are much larger. And also they have TXV on the evaporator coil.
With the TXV, they are supposed to be some what less sensetive to
refrigerant charge. The ones I've worked with come with a freon charge
in the condensing unit. Only have to put some gas in the lines to make
up for long line sets.
Makes me wonder if your guys need some more brazing or Stay-Brite
practice, if one of them is making leaky fittings. I presume you send
a service guy otu to follow up on complaints. What do the service guys
Christopher A. Young
You can\'t shout down a troll.
Really??? And all this time I thought all of the Rheem resi stuff
manufactured after '95 had *SCROLL* compressors. I guess those stickers
that say "SCROLL INSIDE" were just a ruse???
GET A CLUE you ignorant POS!!!!
holy shit cut the guy some slack. he has said in here more than once that
he is a new tech. anybody with any experience knows this means there is a
learning curve for him. instead of stomping on the guy, help him learn.
Before you go and step in something you really don't want on your shoe,
consider that the ignorant POS has been just as ignorant and doesn't *want*
to learn....he has been on here for at least 5 years and hasn't learned a
damn thing. 5 years(or more)...that doesn't constitute a "new" tech.
Care to do a little homework then try again??
i dont care how long hes been here or how long he has been toting a tool
pouch, he has stated his limitations which i feel entitles him to a learning
curve. if he is wrong, correct him. if he is seeking knowledge, teach him.
if he is being an asshole then by all means be an asshole back but i havent
seen that from him, at least not in my time here.
Nathan W. Collier posted for all of us...
I don't top post - see either inline or at bottom.
He has NEVER stated his limitations, as to being wrong, nor expressing his
logic behind a conclusion.
His learning curve looks like this: O
They have; does he benefit from it NO!
Many have have tried - none have succeeded. He is not seeking.
Stick around; you work with him. Teach him something today - will he be able to
apply it tomorrow - NO. Do it privately or publicly whatever...
Let's face it. He has no desire to learn. Like a thief he takes the easiest
way out. He's a "locksmith" who breaks jambs.
YOU make the effort, report back with results.
You and I have known each other a long time....so trust me on this...
Chris is a hack, pure, unadulterated hack.
He is also a trolls, troll. He is trolling, and has no clue he is.
He thinks, and thats THINKS hes offering advice, and over the years, when
called out on bullshit, he ignores it. You can give all the advice you want,
and hes gonna ignore you...unless you offer to convert to Mormanism, drop to
your knees and give a weekly tithe to the little alien mormon hes got under
his magic space suit.
He refers to a job 3 years ago as recent, and cant tell you anything about
real life situations, unless it starts out with: My boss and i.
He is trouble, and while there was a time I thought like you, that time is
......you never called me back, fucker. ;-) gimme a call when you have a
few minutes (i know theyre tough to come by right now), i gotta go over a
few things with you about what we were talking about but i couldnt talk
about because the wifey was in the same room. :-)
On Fri, 11 Aug 2006 08:35:58 -0600, "Nathan W. Collier"
Oh Christ! You're looking at Porn again. :-)
Nathan. Flat rate is the only way. If you dont use it you should
sometime at least try it. You will be very suprised.
Also, remember. YOU do NOT eat your labor or anything else. The
customer pays for EVERYTHING!
(Only exception is if your company truely screwed up. Then you either
fix the problem or get rid of the problem)
in general, yes. i was referencing tech screw-ups/taking to long due to
inexperience. that said, i wouldnt hire anything less than a full
journeyman anyway. my business carries WAY to much liability (from product
loss) to send a newbie.
c'mon Nathan, get a clue. stomin moron has been posting here a hell
of a lot longer than you remember or know, and funny thing, he still
insists he's a new tech...seven fucking years a new tech....
as far as a learning curve, i can understand empathy for mentally
deficient people, if that's what you're implying....
you seem intent on accepting stormin moron is capable of learning, so
try teaching him something....
wait a minute....you're only charging $70 hr for service calls?
shit.....sounds like you and stormin moron may be paddling in the same
i think most anybody is capable of learning if they want to learn.
i charge T&M, minimum 1 hour. $60 hourly rate (ok, i need to update my
website but who has the time this time of year?) + $10 trip charge. i dont
believe in flat rate billing. no two systems are the same, no two problems
are the same, and no two customers should pay the same "just
because".....but thats another issue entirely. i make a good, honest living
by billing T&M.
I almost made a living with T&M but now I actually make a *profit* with flat
rate billing. FWIW, a resi condendser fan motor is still a resi condenser
fan motor and instead of the $150 I used to almost get with T&M, including
the service call and sales tax, now under flat rate, its $363 and
change(installed) including the service call fee and sales tax. I almost
went broke with T&M..... GF opened my eyes.... Thanx Pat :-)
Steve @ Noon-Air Heating & A/C
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.