Just to let you all know - the fault on the kitchen ring main that kept
tripping the RCD was due to the neutrals for that circuit being put to the
non-RCD neutral bus bar.
Thanks very much to all who answered my query.
Well, to answer both Gary and yourself, the final testing and inspection
haven't been carried out yet. Building control sent round a sparky from a
local firm to inspect at first fix. He gave it the ok at that stage and said
that I should call the council when it was ready for final test and
inspection, which I'll be doing on Monday.
I know we shouldn't have energized the circuits yet but the plumber, the
joiner and others need leccy :o)
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.