# Power consumption of 1 ampere

old
replaced!)
Thanks Christain, it is a 6A Tyre B MCB, so I guess my DIY book is out of date.
So I have 1380W available, simply moving the floodlight will cure my worries then.
You may say then why not just switch it off, I would if there was a wall switch for it!
The joys of a new house!
Bill
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

You could save yourself a bit of work by swapping the bulb in the floodlight for a 300W instead of a 500W*.
You say you have either 60W or low energy lamps in you 8 'other' pendants, so:
540W (Big fittings) + 480W (8x60) + 300W (Flood) = 1320W (Panaaaah!)
No it does not meet the letter of the regs, but a degree of pragmatism in these areas works wonders, unless you really _do_ want to have a little play ;-).
* t'missus 'll never notice the difference, particularly if you do it when she's at the shops :) ps: 300W 117mm halogen lamps are avail almost anywhere, and under 2quid if you really look hard.
--
fred

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
wrote:

PIR + Gaffa Tape = Wall switch ;-)

regards Tim
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

The 1A is probably the 12Vdc supply rating. The AC input is likely to around 15W, (about 0.065A) not worth worrying about or moving for now.
--
Steven Briggs

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
Question is wrongly put.
An amp doesn't consume any power. It is a measure of current flowing when a certain power is being consumed and will depend on the voltage being applied.
(Assuming DC or RMS with a purely resistive load)
At 230 volts, one amp will be flowing when there is a load of 230 watts.
At 12 volts, one amp will be flowing when there is a a load of 12 watts.
Power (in watts) = Volts X Amps
Hope that helps....
Nick
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

## Site Timeline

• ### Wickes Kitchens - Beware of their Dodgy software - it will cost you!!!!

• - next thread in UK Do-It-Yourself Forum
• ### OT(ish) - delivery from eBay of small electronic components

• - last updated thread in UK Do-It-Yourself Forum
• ### Does she need a bigger breaker box?

• - the site's last updated thread. Posted in Home Repair
• Share To

HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here. All logos and trade names are the property of their respective owners.