My ideal elan 2 boiler ignites from cold with no problem. However after a period
anything from an hour to longer it refuses to fire up. After a period of time
obviously cools down it will then fire up again.
I initially thought there was a problem with the over heat stat, although this
need to be reset as it does not pop up. However I replaced it with some success
as this morning the boiler fired constantly. However the same problem has
again. I can hear the air pressure switch clicking in and the fan is running but
ignition. Was wondering if it could be a pump problem, maybe the water can not
from the boiler quick enough and its overheating and then is cutting out until
down. However why doesn`t the overheat stat click in ?
Have phoned a round some heating engineers so far none want to know this side of
Would a new pump solve the problem or is my conclusion wrong? Don`t fancy being
consistent heat until after Xmas.
Any help appreciated
Very unlikely to be the pump - if that fails, the overheat stat *will* trip
and the boiler will then do nothing at all.
Does your boiler have a row of (maybe 3) LEDs which come on in sequence
during the firing cycle? If so, how many of these are lit?
The boiler is clearly *trying* to fire - otherwise the fan wouldn't run.
Depending on how far it's getting through the firing cycle you could have a
problem with the pressure switch, pilot solenoid, ignition system or main
gas valve. It's also possible - perhaps even likely in view of the fact that
it seems to be temperature dependent - that you could have some iffy
electronic components on the control board.
Agree with you here if the pump failed completely but the pump is at a guess 13
its pumping but I wonder if its not pumping as efficiently as it once was and
rate through the boiler has been dreuced therefore raising the temperatire
Only one light comes on when a demand for heat is required and this does light
Have put in a new pressure switch and I can hear that switching. The PCB is new
as well so
doubt that is at fault.
I had a similar problem and it was down to the fan ,it did this for a while
then eventually failed completely,I sourced a second hand one from
http://www.cetltd.com really helpfull and saved a load of money to,had it
over a year now and no problems.The owner often contributes on here but have
not noticed him lately.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.