I am getting no heat in the basement zone.I thought the thermostat may be
faulty,but taking it off the wall and touching the two wires together didnt
even create a spark.Opening the zone valve manually didnt even initiate the
circ. pump.The other two zones work great.
My question is...If the zone valve is gone,would that prevent voltage
getting to the thermostat?
thanks in advance!
no,it's a honeywell v8043g.
I swapped a powerhead from a working zone and it worked.Guess I need a new
powerhead today.Nice guy I am my daughters now have warm rooms and mine is
16c this morning.I will get one today...no Sunday shopping here in Nova
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.