# Switch polarity question (electrical)

It's not an actual polarity you want; remember, this is ac. The "polarity" applies to which is hot and which is neutra.
Arbitrarily assign one as Hot (H); use the wire to the hot connection on the fixture as H: Find an Earth Ground (receptacles are probably earthed). Then, check H - N 120V H - Earth 120V N - Earth 0V
If H - N = 0 then N - Earth should be 120V, meaning they are reversed. Switch the wires with each other.
Assumption: Neutral and Earth are ONLY joined back at the breaker box and nowhere else! Validate Earth connection by turning off all power (Mains). Use your ohmmeter to measure the resistance between Neutral and Earth. It should only be a few ohms, depending on the length of wire involved, or maybe 0.0. SWITCH YOUR METER OFF OHMS AS SOON AS DONE, so you don't accidentally try to measure voltage with it. The reason to turn off all power is that, should the polarity be wrong, you will fry your ohmmeter. I always check first for voltage and only after knowing it's not 120 V ac do I switch it to ohms. Then as soon as I finish ohmming thngs out, I put it back to measure ac voltage.
HTH
Twayne
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

That would be my quick suggestion also. Find a ground somewhere. connect one side of your meter or one side of light bulb to that. With lights switched on.
Any wire wire that has potential to that ground is most likely the live (today black) wire and is either a direct live from the supply fus/breaker or a switched live.
The wire that has zero or a very low potential to that ground (although even cheap digital multimeters can be deceiving) is most likely the neutral (white wire).
Don't mess around with readings of 30 or or some odd voltage on wires which are disconnected or switched off. In fact a light bulb is often a better tester than a meter that can pick up odd induced voltage from other circuits or wires!
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

## Site Timeline

• ### Kitchen faucet chatter

• - next thread in Home Repair
• ### caulk ,grout,or mortar

• - previous thread in Home Repair

• ### Wing mirrors on cars

• - last updated thread in Home Repair
• ### Can I just disconnect the MR16 GU5.3 halogen downlighters and leave the bulbs in situ?...

• Share To

HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here. All logos and trade names are the property of their respective owners.