Hi one of the 2 Lennox THA090 rooftop compressors is not running even though we set the temperature really low. The office still feels warm. We opened the cover and confirmed that one of them is running and the other is not.
However the 2 PCB control boards all seem to indicate everything is fine, based on the LED blink pattern. Any clue? Thanks a lot!
How do we test if the compressor is really broken?
The unit is about 10 years old.
On 9/3/2015 12:58 PM, email@example.com wrote:
The usual. Check for power supply, amp draw.
Disconnect, and check for open circuit, or
short to ground. Check the run cap while you
are in. Nothing challenging, here.
Christopher A. Young
learn more about Jesus
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.