i can read 120v
between hot & ground at the outlet ,my house
has been built in 1952 and has some old wiring although there was an
addition to it,and a bigger breaker box 100amp
my light bills are high as well i wonder if there is a leak of voltage
some place, help please.
On May 27, 1:32 am, firstname.lastname@example.org wrote:
Hot and ground should read the same as hot to neutral. Or very near
the same. The neutral buss (bar) in the breaker box is stake grounded
or street-side water pipe grounded. Neutral and ground are then at the
same potential. (the same potential as the center-tap of your utility
What you say "sounds" normal.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.