** The OP simply has to make sure any varistors are rated at 275VAC,
suppression caps have the same voltage rating and are marked class X1 or
2 - oh, and neon lights must have series resistors of 180 kohms or higher.
Varistors must only be wired from active to neutral, never to ground.
If in doubt, just remove the lot with side cutters.
What's dead simple is that you should NEVER used stuff rated for a max
on higher than 120V...PERIOD.
Emphasis on the DEAD.
Whether it works is irrelevant.
It's ill-advised, dangerous, prone to fire, illegal,
probably voids your insurance...and then, there's that dead part.
It's not a self-regulated process that rids the world of idiots.
When you burn the place down, your reckless incompetence seriously
Get properly rated equipment...PERIOD!!
Take it from someone who was completely burned out by the idiot
in the adjacent apartment.
On 5/22/2014 3:24 PM, mike wrote:
<snip> > What's dead simple is that you should NEVER used stuff rated for a max
It's actually none of those.
A "properly rated" 240V power strip would have thinner conductors. It
would be no more dangerous because it would also have a lower amperage
Whatever caused the fire it was certainly not someone using a 120V power
strip on 240V.
As many others have pointed out, the power strip is actually safer on
240V because the current is much lower for the same wattage.
However the downside is that it would be possible to overload the 240V
circuit, which is probably not a 15A circuit, and the circuit breaker in
the power strip would not blow (but the circuit breaker in the breaker
panel would trip).
It's people like you, making grand declarations based on PART of the
problem that cause so much grief in the world.
There are many people who will actually believe that you told them
it was safe.
The other issue is that the internet is forever. Years from now,
some newbie does a google search and sees your missive out of context.
What is it about doubling the voltage on a system and routing it to
sockets that invite you to plug in devices rated at half the voltage
do you think is a good idea?
Think back about all the screwups in your past.
The things you thought about and carefully analyzed are usually NOT
the things that caused you grief.
It's the things you didn't consider that cause most of the problem.
Must be nice to be all-knowing.
Sorry about the tone. I get upset when people advise stupid things
that might result in harm to others.
All true, but that's a lot of work to avoid buying a 240V power strip. A
lot of the lower cost strips can't be easily opened either.
I like this one <(Amazon.com product link shortened)> which gives you
three U.S. outlets and 2 USB ports that provide a total of 1.5A. Enough
current to charge a tablet and a phone though not enough to be using the
device at the same time as it's being charged. Very compact. Still need
a plug adapter though.
** My post was basically facetious - pointing out that one has to be expert
in identifying components like varistors and X1 caps in order to " .. check
there is nothing that might not like 240V in it ".
** Well, all the parts I mentioned would fail quickly if not rated for 240V
There might be a loud bang, but definitely no fire hazard.
** That must have been very distressing.
Every electrical plug on board Carnival's ships (and a lot more)
will accept both 240 euro (round pin), Japanese 240 (parallel blade)
and American 120 volt parallel blade plugs.. They are labeled 240
So do the same with the power bar.
It is NOT a safety issue unless it becomes a stupidity issue.
On 5/22/2014 6:54 PM, firstname.lastname@example.org wrote:
Virtually EVERY safety regulation is about preventing stupid people
from doing stupid things that might hurt themselves or others.
If you need something done right, look no further than Carnival Cruise
Next time you get pulled over for speeding, explain to the cop
that the other guy was speeding too. See how far that gets you.
Just because someone else does it, doesn't make it a wise thing to
The attitude expressed here is common. I've had to beat
it out of virtually every engineer I've trained.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.