I am trying to fix a Day & night split system. I bypassed the T-stat to
turn on the Heater. The pilot and main burner turns on, but as soon as the
blower turns on the burners go off and the blower keeps running. I changed
the main control board and checked all the safty switches. What could it
I would not say always. I try and I try to qualify my comments when I
know I am guessing. I also try to admit when I am wrong and to learn from
those situations. I think that is the best anyone can do.
On Fri, 12 Jan 2007 07:20:06 -0500, "Joseph Meehan"
Actually I have the ransley idiot blocked so I usually don't see his
posts. if you were to look I don't post on the hvac group because I
don't agree with their methods or flaming in that group. so I am Not
"From" the hvac group. And no, Meither one of you gives good advice!!
If you don't know it is better to not answer at all as someone may
follow your advice and either hurt themselves or damage their
equipment. I know you really don't care about this as you still keep
giving out wrong advice without any warnings. the real scary thing is
that you probably think it it correct.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.