I finished wiring up my 3 way switches I asked about a while ago, but the
one switch only worked in one position. I assumed I had a common and
traveller reversed somewhere, but the wiring seemed fine. I finally pulled
both switches to check continuity and the same push connector was bad on
both switches, as well as a third switch I have for another circuit. I
changed to the screw connectors on both switches and all is beautiful now!
Thanks to Terry and RBM for the original help. I did end up cutting out the
entire ceiling betyween the two fixtures as you suggested. :-)
Guess you didn't mention you would be backstabbing it to hook it up. If
you did you would have got many one word replies - "Don't".
Someone please tell me why they even put that options on?! They are
notorious for failing as well as a fire and safety bombshell waiting to
go off, yet, code must allow it.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.