Looks fairly easy to install where I just took the old one out. But
the old one has two wires coming into it, one black, one white. The
instructions for the new one (hasn't arrived yet) shows three wires,
with the third one attaching to a screw on the dishwasher's electrical
Since I only have two coming up from the house panel, can I just run a
wire to something that should be grounded, maybe the drain pipe?
If it's BX, I wouldn't worry about it. The armor shield would act as a
If it's ungrounded Romex, you could run a seperate ground back to the
panel ( not a pipe), or simply replace the existing breaker with a
GFCI breaker which would provide protection in the abscence of a
On Tue, 15 Apr 2008 10:53:11 -0700 (PDT), Mikepier
Hmm. No, these are fuses. The wire is (having just looked up Romex and
BX) BX. A white and black wire inside a metal snake-like housing. Then
it sounds ok as is, with the metal sheath providing the grounding.
That's how it was hooked up.
No, you need a proper ground, particularly with a device like a
dishwasher. What kind of wire is currently servicing (or was servicing)
the dishwasher? Unless it's pretty old, it should have a ground
conductor, possibly the person who installed the previous dishwasher
didn't connect the ground and cut the ground back for some reason.
re: I have a BX cable and that should be sufficient...
...assuming the BX is conected to a chassis ground at one end and an
earth ground at the other. Simply sheathing the wires in a metal
casing that is connected to nothing grounds nothing.
Just making sure we cover all bases here...
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.