Experiment: Swap the "hot" dimmer with one of the other "cold"
dimmers. Inspect the wiring while you're at it for obvious loose/bad
connection. If the "hot" dimmer's now cold and the "cold" dimmer's now
hot, it's possibly the load. If the "hot" dimmer's still hot, it's
possibly a bad switch, replace it.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.