Good point, Erik. I have seen that with the bad aluminum wire where the
electrician looped through the outlets. The outlet that fried had
nothing plugged into it; the load was from downstream.
This is Turtle.
Replace the receptical and both plug for the stuff plugged into it. When you
have hot plugs on a light load, you usely looking at a loose connection or a bad
connection on the receptical.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.