Don't worry I'm running to a subpanel in the garage. Thanks for the
recommendation on the ENT tubing, now I've got the whole project figured
out. I was struggling with the transition from the main breaker to the
Schedule 40, now it's a no brainer. Thanks again to everyone for posting,
you've really helped me out! Please keep on answering questions!
Good luck then. Make sure the neutral and ground bus are NOT bonded
together at the subpanel, It is a common mistake. The neutral and the
ground bus should only be bonded at the main service entrance.