Hello ... probably the only thing I don't understand is how a neutral
is NOT required on a 220V line to operate at 220.
A normal 110 circuit terminates at the panel with white to common and
black (hot) to breaker. When a motor is turned on, I understand
current *flows* from neutral to hot (even though it's AC, it flips 60
times a second; not dealing with AC?) I assume this is just
I have a 220V air compressor (2 hots, 1 ground) and it has no return,
which is OK since there's no device requiring 110 (one leg). How can
current flow with just 2 hot wires? I assume the 2 incoming "hot bars"
(from outside) are in sync. Both bars are either positive or negative.
So, when the "negative" phase occurs, where does the current drain? I
can see how the ground will work... and maybe it *IS* used.
Can someone clarify?
Thanks a lot! I greatly appreciate it.
AC reverses polarity 120 times per second. So for 1/120th of a second, one
wire is +, and the other is -. I like to think of it as the "push-pull"
effect. At any givin half-cycle, one is pushing(+), and the other is
With one hot wire to ground, only that one wire pushing or pulling on it's
own at any givin half-cycle. When the circuit is closed, the ground or
neutral is sorta forced into push/pull action, except it isn't really
pushing/pulling it's own electricity on it's own, so the voltage is half, or
Generally you have 3 wires coming into your home, one of which is neutral.
Across either of the other 2 wires to neutral is ~120 VAC. But between
the 2 hots is ~240 VAC. So be careful about connecting one hot to another
hot, because if they are different hots, it could be a 240 volt short.
So yes you do have 2 hots with 220/240 V and neither of them should be
grounded. But at an given instant (except in middle of AC cycle) they are
opposite polarities, so current will flow between them.
David Efflandt - All spam ignored http://www.de-srv.com /
http://www.autox.chicago.il.us/ http://www.berniesfloral.net /
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.