Having some trouble with a 25 ton AC system. After a few minutes of
running the compressor starts cycling very quickly - on and off every
3 seconds or so. When it's doing this the supply pressure guage show a
fairly steady 130 psi. The suction pressure guage rises to about 40
psi when the compressor is running and drops to about 20 psi when
stopped. It's not HP cut out, the condenser is getting plenty of
cooling water. It's not motor overload either. What's going on?
Expansion valve not opening properly?
Any suggestions appreciated...
Thanks for all the help and concern. Don't worry, I've switched to the
other system for now. An LPCO is on the way. I'm also interested in
how things work so when the compressor is doing funny things my
curiosity is piqued. What would cause the suction pressure to drop so
quickly? Refrigerant can't be getting round the circuit quickly enough
to keep the suction pressure up. This is why I think the expansion
valve is blocked or not opening properly. Or possibly an undercharged
system but it has been working perfectly up till now and this problem
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.