I have a Lennox Elite gas furnace and I need help please quickly......
my furnace broke down last night and it is -15degrtees here....I have
alternating red-green flashiong lights and no glow at all...there is a
clicking sound intermittently as the furnace tries to start, but that
is momentarily. No heat at all.....the fan works if I put it on "fan-
setting", can anyone help with suggestions...PLEASE......???
Model G26 or 9OU furnace. Blue jhonston control module. Spark ignition.
Alt fast flash = ign. failure. Who doesn't pay attention to LED's?...idiot
Could be the clicking is establishing the pilot, but flame sensor is dirty, or
module is bad, or gas valve is bad. You sure your gas hasn't been shut off?
Those blue module's all fail sooner or later. Replace with honeywell
Lennox will have a kit no doubt. Nothing you can easily do to get it going.
I wouldn't even walk someone through cleaning that sensor....putting the
burner door on wrong can cause probs...and most pro's can't seem to do it
--------------------------------- --- -- -
Posted with NewsLeecher v3.8 Final
Web @ http://www.newsleecher.com/?usenet
------------------- ----- ---- -- -
On 06 Feb 2007 00:38:33 GMT, DANgER ( firstname.lastname@example.org) wrote:
Now thats funny. You gotta watch an idiot light to figure out whats
wrong. Id love to see you check one out giving a false code (which
happens very ofter). I'll bet you go through boxes of those 3amp one
time fuses. What a nut hole. Nobody trusts a blinking LED you retard.
I hope your mother told you you were a pathetic waste of sperm.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.